|Temperature monitoring range||0 - 99°C|
|Temperature of the TW container||30 - 80°C|
|Pump start delta||0 - 30°C|
|Pump stop delta||0 - 20°C|
|Pump power control||20 -100 %|
|Pump start forcing ability|
|Collector sensor cable length up to customer requirement|
Microprocessor controller MTS8 solar is a unit to control the heat container feeding pump in solar installation. Controller warms up the container on the basis of a collector and container temperature difference and additionally protects collector and container against overheating. The unit protects collector starting pump if collector temperature reaches 99°C and protects container directing the heat excess back to the cold collector e.g. at night. A silicon cable at the end of collector sensor is high temperature and external environment resistant.